LOGAMATIC 4121 PDF
Download the catalogue and request prices of Logamatic By buderus, heat regulation and hygrometric control, logamatic Collection. Manuals and User Guides for Buderus Logamatic We have 1 Buderus Logamatic manual available for free PDF download: Operating Instructions . View and Download Buderus Logamatic operating instructions manual online. Logamatic Control Unit pdf manual download. Also for: Logamatic.
|Published (Last):||3 August 2006|
|PDF File Size:||3.75 Mb|
|ePub File Size:||19.23 Mb|
|Price:||Free* [*Free Regsitration Required]|
You may select either an individual heating circuit or all circuits assigned to the MEC2. The selected permanent display has now been saved. Adjusting the room temperature for day mode Press “Day mode” to select the standard heating mode day mode.
The switching point to be deleted is displayed. Enter the length of time the system should only heat to the preset room temperature. 41121 Mode Logamatic Fig.
Heat regulation and hygrometric control LOGAMATIC Logamatic Collection By BUDERUS
This will be subject to the outside temperature, the building insulation and the room temperature setback. Simple Troubleshooting — DHW is set to the wrong temperature.
External sensor fault Flow sensor fault The heating system may heat with higher temperatures to safeguard the heat supply. The primary and secondary pumps and the DHW circulation pump are switched off. Tell your heating contractor which temperature sensor is faulty.
Coppers pig-iron Logamatic 4121/4122
This pump enables the second heating circuit to be operated independently of the first heating circuit. The standard functions are: Your heating system offers a wealth of further useful functions. The display shows “Constant winter”. Display Heating circuit pump operational Display Cylinder primary pump operational Display DHW circulation pump operational Display Thermal disinfection enabled Logamaticand – Subject to technical modifications. DHW heating remains operational. The heating circuit pump or cylinder primary pump as well as the DHW circulation pump are switched off.
What does the control unit calculate? When changing from total shutdown to reduced heating, total shutdown is activated subject to outside temperature when the actual outside temperature exceeds the set outside temperature.
Page 86 Notes Logamaticand – Subject to technical modifications. By pressing ‘print’ button you will print only current page. Hold down llgamatic, and select the required permanent display with the rotary selector here: The modified switching point will be saved under the “Own” program and the number of the heating circuit here “2”.
Setting the operating mode for DHW circulation. What are heating circuits? Fault message “Time switch not possible” Fault messages. Selecting A Standard Program here “Senior program”. Creating a new DHW circulation pump program. Please observe these notes.
Setting the time Hold down “Time”, and select the required time with the rotary selector. Therefore, check whether the doors and windows are correctly sealed.
Notify your contractor of the faults displayed on the MEC, or the fault code on the boiler. The primary and secondary pumps and the DHW circulation pump are switched off.
If required, your heating contractor can alter these settings. The set temperature is displayed via an LED next to the rotary selector. In this case, the radiators lgamatic supplied at a higher flow temperature than the underfloor heating system. Press “Back” to return to the permanent display. The pause function starts immediately.
With this kind of control you will also need to keep all thermostatic radiator valves in the reference room fully open. A pump installed in the flow line circulates the heating water.
Page 73 The heating circuit pump or cylinder primary pump as well as the DHW circulation pump are switched off. AUT z Open flap. To be able to utilise room temperature-dependent control, you need a room that is representative of your whole home. Turn the rotary selector to the required day room temperature here: AUT Your modified program will be saved under the program name “Own” and the number of the heating circuit.
Family program The logamatci switching point start point: Mixers can be manually set. Isolate the heating system from the mains supply with the emergency stop switch upstream of the boiler room, or by removing the main fuse.
The mixer is switched volt-free. When no blocks are left both heating phases have been combined. Don’t show me this message again. Page 37 – Selecting and modifying a heating progra This saves you energy. This will be saved under “Own” and the number of the heating circuit.